One of the most popular manufacturers that produce thermostats is White Rodgers. Being established by a group of Emerson engineers, the company has produced thermostat products since 1936. With years of experience in the industry, White Rodgers has embraced a lot of loyal clients across the globe.
However, nothing is perfect in this world, not to mention the thermostat from White Rodgers. The most common issues found on White Rodgers thermostat often associated with cooling or no heat. So, how to fix the problems?
Find out the White Rodgers thermostat troubleshooting along with the common problems and solutions on the following page.
Table of Contents
Troubleshooting No Heat
What will you do if you find no-heat problems on your White Rodgers thermostat? Well, just don’t rush to call a technician or the installer. Depend on the levels of the problems, you might be able to fix the no-heat issues by yourself.
Not only money-saving but being able to repair the existing problem on your thermostat by yourself will give you a feeling of satisfaction. So, what you need to do with the White Rodgers thermostat troubleshooting when finding the no-heat issue on the device?
Well, first of all, you need to identify the possible causes of no-heat issues. Several factors that contribute to the emergence of the problem include:
- Tripped Circuit/ Blown Fuse Breaker
If the no-heat problem is caused by the tripped circuit or blown fuse breaker, there is nothing you can do to fix but replace the reset or fuse breaker.
- Low Batteries
Low batteries can also lead your thermostat to experience no-heat issue. If it becomes a problem, you are suggested to replace the battery.
- Loose Connection to the System
All you need to do to fix the problem is to tighten the connections to fix the no-heat problem in your thermostat.
- Furnace Power to Switch Off
When your thermostat doesn’t produce heat, you need to check the furnace power. There will be no heat produced if the furnace power is in “off” mode, so turn it on.
- Improper Installation or Panel Loose on the Furnace Blower Compartment Door
Make sure you properly install the furnace blower compartment door of the thermostat. It is aimed to improve the safety interlock of the device. Then, check if there is a panel loose on the compartment.
- The Broken Anticipator Wire
The broken or melted anticipation wire can also cause the device to fail to produce heat. It can be caused by the dead short or excessive current in the system.
White Rodgers Heat Pump Thermostat Troubleshooting
What do you need to do with the thermostat troubleshooting to fix problems found on the heat pump? Well, the first thing you can do is ensure that the pump is properly tightened. This is also important to check if there is any leak found on the pump. If that becomes a problem, you need to replace the pump so that the thermostat can operate normally.
Troubleshooting No Display
Another common problem found in the thermostat is the absence of display. So, what is White Rodgers water heater troubleshooting needed if there is no display seen on the device? When the display does not turn on, you need to check if you have properly connected the thermostat. Then, make sure that you also check the power supply available in the electrical panel of the device.
But, what if the display turns on and off constantly? Well, if that becomes the case, you need to check whether the heating unit of the thermal protection has opened accidentally because of overheating. Another thing you should do is check to find out if the heating unit is still in good condition of operation.
The lower performance of the heating unit can also cause the display to turn on and off constantly. You also need to know that the clearance around the device will depend on the specifications of the manufacturer. But, if you find that the display comes with a relatively low contrast when the heating is on, you need to check the load.
If it is lower than the minimum load, the device will only produce a low contrast display. To fix the problem, you need to install a heating unit that has load above the limits required by the thermostat.